- Report: #931555
Report - Rebuttal - Arbitrate
Complaint Review: magic touch mechanical arizona
magic touch mechanical arizonaP.O. Box 20207 Internet United States of America
magic touch mechanical arizona Bad treatment poor quality work and just a ripoff http://www.airconditioningarizona.com/contactus.ph, Arizona
*UPDATE EX-employee responds: Do you think everyone is as dumb as you?
*UPDATE EX-employee responds: Real Truth
*UPDATE EX-employee responds: Someone who knows this company well
*Consumer Comment: RICH MORGAN FULL OF HIMSELF
*REBUTTAL Owner of company: Inspection Results from Arizona State Inspector
*Author of original report: real truth about BBB
*Author of original report: not true
*REBUTTAL Owner of company: Truth Be Told
A business' first
line of defense
on the Internet.
If your business is
willing to make a
Click here now..
Feels like extortion, as they had to know the work was going to cause this issue. Their site says they do energy audits and duct sealing for better efficency yet when I had inspectors come look there were leaks no seals and water damage. The ductwork was thrown in and not properly distributed using drop boxes . They also insisted on a second return which was place within 5 feet or the original the needed a 20x30 opening for this return but when you open and look in the duct is compressed to half that size. [continued below]....
ROOFTOP UNIT: AIR LEAKS AROUND ALL PANELS. LIQUID TIGHT AND ELECTRICAL WIRES ARE NOT REPLACED. CONDENSATE LINE IS NOT CLAMPED AND SECURED.
DUCTWORK IN ATTIC: METAL JOINTS (T Y'S) ARE NOT INSULATED CAUSING CONDENSATION. (THIS WILL CAUSE DAMAGE TO FLEX DUCT AND POSSIBLY DRY WALL. JOINTS ARE INSTALLED IMPROPER AND POSITIONED SO THAT SOME REGISTERS RECEIVE MUCH MORE AIR THAN OTHERS. DUCT WORK TO KITCHEN/DINING ROOM HAS BEEN IMPROPERLY INSTALLED TO NOTALLOW ENOUGH AIR TO FLOW IN THERE DIRECTION. ALL ATTIC DUCT WORK WILL NEED TO BE DISCONNECTED AND INSTALLED PROPERLY. RETURN AIR VENT SHOULD BE ADDED TO DINING ROOM AREA.
THERMOSTAT: NOT POSITIONED PROPERLY AND HAS A HOLE BEHIND IT CAUSING ATTIC AIR TO ALTER TEMPERATURE READINGS.
stay away unless you want to be treated poorly and end up worse off than before.
This report was posted on Ripoff Report on 08/23/2012 12:21 PM and is a permanent record located here: http://www.ripoffreport.com/r/magic-touch-mechanical-arizona/internet/magic-touch-mechanical-arizona-Bad-treatment-poor-quality-work-and-just-a-ripoff-httpw-931555. The posting time indicated is Arizona local time. Arizona does not observe daylight savings so the post time may be Mountain or Pacific depending on the time of year.
If you would like to see more Rip-off Reports on this company/individual, search here:Search Tips
In order to assure the best results in your search:
- Keep the name short & simple, and try different variations of the name.
- Do not include ".com", "S", "Inc.", "Corp", or "LLC" at the end of the Company name.
- Use only the first/main part of a name to get best results.
- Only search one name at a time if Company has many AKA's.
Advertisers above have met our
strict standards for business conduct.